Drive Motor for Forklift - Motor Control Centers or MCC's, are an assembly of one enclosed section or more, that have a common power bus mostly consisting of motor control units. They have been used since the 1950's by the auto business, for the reason that they utilized lots of electric motors. Now, they are used in other industrial and commercial applications.
In factory assembly for motor starter; motor control centers are somewhat common technique. The MCC's include variable frequency drives, programmable controllers and metering. The MCC's are usually seen in the electrical service entrance for a building. Motor control centers often are used for low voltage, 3-phase alternating current motors which vary from 230 V to 600V. Medium voltage motor control centers are intended for big motors which range from 2300V to 15000 V. These units make use of vacuum contractors for switching with separate compartments so as to attain power switching and control.
In areas where very dusty or corrosive processes are happening, the motor control center could be installed in a separate air-conditioned room. Normally the MCC will be located on the factory floor adjacent to the equipment it is controlling.
For plug-in mounting of individual motor controls, A motor control center has one or more vertical metal cabinet sections with power bus. To complete maintenance or testing, extremely large controllers could be bolted into place, whereas smaller controllers can be unplugged from the cabinet. Each and every motor controller consists of a contractor or a solid state motor controller, overload relays to be able to protect the motor, circuit breaker or fuses to be able to provide short-circuit protection as well as a disconnecting switch to be able to isolate the motor circuit. Separate connectors enable 3-phase power to enter the controller. The motor is wired to terminals located in the controller. Motor control centers provide wire ways for power cables and field control.
In a motor control center, each and every motor controller can be specified with several various alternatives. Some of the choices consist of: pilot lamps, separate control transformers, extra control terminal blocks, control switches, and numerous kinds of solid-state and bi-metal overload protection relays. They likewise have different classes of kinds of power fuses and circuit breakers.
Regarding the delivery of motor control centers, there are a lot of options for the customer. These could be delivered as an engineered assembly with a programmable controller along with internal control or with interlocking wiring to a central control terminal panel board. On the other hand, they can be supplied ready for the customer to connect all field wiring.
Motor control centers usually sit on the floor and should have a fire-resistance rating. Fire stops can be necessary for cables that penetrate fire-rated floors and walls.
Click to Download the pdf